Caltrans Bidding Connect Account:
Sign In (Sign in is required to access Project Plans)
Create Account (Click here to create a Caltrans Bidding Connect Account)
Viewing inquiries for 11-2N1084Submit new inquiry for this project
Inquiry #1: On General Plan #2 De Anza Off-Ramp- UC, the Prep, Furnish, and Place Quantities which then affect Unsound quantities appear to be incorrect.
Please adjust to match the measurements shown on the drawings.
For example, Perp and Place 17,422 SF should be 14,542 SF and Furnish 1742 CF should be 1454 CF, and Unsound 1% 44 CF should be 37 CF
Inquiry submitted 08/17/2023
Submitted for consideration.
Response posted 08/17/2023
Unless an addendum is issued, please bid per the current contract bid documents.
Response posted 10/03/2023
Response #3:Please refer to Addendum No. 2 dated October 26, 2023.
Response posted 10/26/2023
Response #4:Quantities has been revised on sheet 20 of 22 of the contract plans.
Response posted 10/31/2023
The information provided in the responses to bidder inquiries is not a waiver of Section 2-1.07, "JOB SITE AND DOCUMENT EXAMINATION" of the Standard Specifications or any other provision of the contract, nor to excuse the contractor from full compliance with the contract. Bidders are cautioned that subsequent responses or contract addenda may change a previous response.